Low price 100 hp soft starter, 75 kW three phase 230v, 420v, 480v, 690v for selection, control motor in soft start & soft stop, direct sale by manufacturer.
Delivery date: 15 - 30 Days
100 hp AC motor soft starter, 75 kW three phase 230v, 420v, 480v, 690v for selection.
||GS2-075 (230v), GS3-075 (420v), GS4-075 (480v), GS6-075 (690v).
||100 hp (75 kw)
||3 phase 230v, 420v, 480v, 690v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Soft Starter vs Variable Frequency Drive
Not all soft starters use a simple reduced voltage principle. For a number of years now, advanced soft starters (including the units manufactured by Gozuk), have used 'torque control' that produces a far better starting and stopping characteristic. While variable frequency drives (VFD) produce excellent soft starting and stopping functions (sometimes with extremely low starting current), they are expensive solutions if variable speed is not required - particularly on large applications. Also, the skill level required to 'correctly' commission variable frequency drives is far greater than it is for soft starters. They both have their place and as a supplier and systems integrator for both technologies, we have to be smart enough to know which one to recommend to our customers.
Write your own review for 100 hp (75 kW) Soft starter, 230v/420v/480v/690v