10 hp soft starter, 7.5 kW 3 phase 220v, 380v, 480v, 690v electric motor soft starts, protecting AC motor from over-voltage, over-current and phase unbalance etc.
Delivery date: 6 - 12 Days
10 hp motor soft starter, 7.5 kW three phase 220v, 380v, 480v, 690v.
||GS2-7d5 (220v), GS3-7d5 (380v), GS4-7d5 (480v), GS6-7d5 (690v).
||10 hp (7.5 kw)
||15 amps at 380/480v, 30 amps at 220v
||Three-phase 220v, 380v, 480v, 690v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Choose Soft Starter or Variable Frequency Drive?
Although both variable frequency drive (VFD) and soft starter can reduce inrush voltage during induction motor starting, but soft starter can not control the frequency added to the motor, soft starter just helps to lower the induction motor starting current and smoother the start up, whereas VFD can control the frequency and it's much more intelligent and it has all the functions of soft starter. As long as the motor requires vary speed, VFD is the choice, otherwise you can go for soft starter. In case of the budget is not an issue and proper investigation of application, you may select VFD instead of soft starter.
Write your own review for 10 hp (7.5 kW) Soft starter, 220v/380v/480v/690v