Discounted 125 hp soft starter, 90 kW three phase 220v, 380v, 460v, 660v AC motor starter, control motor in soft start & soft stop, buy it from Chinese manufacturer directly.
Delivery date: 15 - 30 Days
125 hp motor soft starter, 90 kW three phase 220v, 380v, 460v, 660v AC motor starter.
||GS2-090 (220v), GS3-090 (380v), GS4-090 (460v), GS6-090 (660v).
||125 hp (90 kw)
||3 phase 220v, 380v, 460v, 660v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Choose Soft Starter or VFD?
When you can choose a variable frequency drive (VFD) to start an induction motor, it kinds of expensive compared to a conventional soft starter if your application running at full speed all the time and there is no need for flow or speed control. A motor soft starter achieves almost the same current limit and reduced water hammer effects by controlling just the voltage to the induction motor. Many soft starters have a contactor that bypasses the thyristor bridge once the motor gets to required speed.
Write your own review for 125 hp (90 kW) Soft starter, 220v/380v/460v/660v