Cheap price 40 hp soft starter for sale, 30 kW three phase 240v, 420v, 480v, 660v AC motor soft starter, make motor in soft start & soft stop, buy from manufacturer directly.
Delivery date: 6 - 12 Days
40 hp soft starter, 30 kW three phase 240v, 420v, 480v, 660v AC motor starter.
||GS2-030 (240v), GS3-030 (420v), GS4-030 (480v), GS6-030 (660v).
||40 hp (30 kw)
||3 phase 240v, 420v, 480v, 660v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Soft starter is better than VFD regarding Harmonics effects
Motor soft starter does help in reducing inrush currents, most soft starters come with an adjustable kick current to overcome the initial inertia needed. Once up to speed it does switch over to being across the power grid. Be careful here if you ever expect to start ATL, the manufacturers generally reduce the size of the bypass contactor. Harmonics are nasty as well running through the SCRs during the start sequence. Variable frequency drives (VFD) come in a variety of front ends from 6-pulse, 12-pulse, 18-pulse, and active front ends. Harmonics are present in all variable speed drives applications so be aware of these and their effects.
Write your own review for 40 hp (30 kW) Soft starter, 240v/420v/480v/660v