Inexpensive 50 hp soft starter, 37 kW three phase 230v, 380v, 460v, 690v for selection, protect AC induction motor from inrush current impact, buy from Chinese manufacturer directly.
Delivery date: 6 - 12 Days
50 hp AC motor soft starter, 37 kW three phase 230v, 380v, 460v, 690v for selection.
||GS2-037 (230v), GS3-037 (380v), GS4-037 (460v), GS6-037 (690v).
||50 hp (37 kw)
||75 amps at 380v/460v, 150 amps at 220v
||3 phase 230v, 380v, 460v, 690v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Choose between soft starter and variable frequency drive
Soft starter is used to decrease the starting current of the induction motor and decrease the tensions. However, variable frequency drive (VFD) is utilized when you have to control the speed, torque... of the induction motor during a process. Generally, when we use a soft starter to accelerate an induction motor to its operating speed (97% synchronous speed), then we by-pass the soft starter. The motor normal operation is same as cross-the-line operation.
Generally VFD is used continuously to change speed, whereas soft starters are only for reducing starting surges, so as a whole VFD fulfills both purposes during starting as well as normal running if budget is not concerned.
Write your own review for 50 hp (37 kW) Soft starter, 230v/380v/460v/690v
Please'd like to know the time of delivery of this equipment.
on 08/04, 2015
Was this review helpful?