Low price 60 hp (45 kW) VFD, three phase 240V, 380V, 480V energy saving variable frequency drive with high performance, brand new direct sale by Chinese manufacturer with fast delivery.
Delivery date: 15 - 30 days
60 hp (45 kW) high quality variable frequency drive, three phase 240V, 380V, 480V for selection.
||60 hp (45 kW)
||3 phase 240V /380V /480V AC ±15% (Optional)
||3 phase AC 0~input voltage
|Over load capacity
||150% of rated current for 1 minute, 180% of rated current for 3 seconds
Sensorless vector control;
||150% of rating torque at 1 Hz
|Speed control accuracy
||≤±0.5% of rating synchronous speed
||Digital setting: max frequency x± 0.01%;
Analog setting: max frequency x± 0.2%
||Analog setting: 0.1% of max frequency;
Digital setting: 0.01Hz
||Automatic torque boost, manual torque boost 0.1%~30.0%
|Interior PID controller
||Be convenient to make closed-loop system
|Automatic energy save running
||Optimize V/F curve automatically based on the load to realize power save running
|Automatic voltage regulation (AVR)
||Can keep constant output voltage when power source voltage varies.
|Automatic current limiting
||Limit running current automatically to avoid frequent over-current which will cause trip
||–10℃~ +40℃; VFD will be derated if ambient temperature exceed 40℃; each rise 1℃, the derate will be 5%
||5%-95%, without condensation
||≤1000m; VFD will be derated if above 1000m
|Impingement and oscillation
||Normal running:<5.9m/s2 (0.6g); Transportation:<15m/s2 (1.5g)
||–20℃~ +60℃; no dust, no corrosive gas, no direct sunlight
Tips: Choose between Variable Frequency Drive and Soft Starter
I would like to say that variable frequency drives (VFD) are not always the best way of saving energy. If the induction motor is running at full speed it is sometime more efficient to use a soft starter or fixed speed motor controller. Of course if the application can be slowed down then VFD is a very good solution.
If the load is required to run at full speed all the time then using a VFD is less efficient and in fact will introduce losses that a soft starter would not. We approach the market that there are different products for different jobs, sometimes VFDs are the best solution and sometimes soft starters are, it all depends on what the client wants to achieve.
Write your own review for 60 hp (45 kW) VFD, 3 Phase 240V, 380V, 480V