75 hp soft starter, 55 kW three phase 240v, 440v, 480v, 660v AC motor softstarter to protect motor from inrush current impact, buy it from manufacturer directly with wholesale price.
Delivery date: 15 - 30 Days
75 hp motor soft starter, 55 kW three phase 240v, 440v, 480v, 660v for selection.
||GS2-055 (240v), GS3-055 (440v), GS4-055 (480v), GS6-055 (660v).
||75 hp (55 kw)
||3 phase 240v, 440v, 480v, 660v AC
||Squirrel-cage three-phase asynchronous motor
||It is recommended not to exceed 20 times per hour.
||(1) Operation panel control. (2) Operation panel + external control. (3) External control. (4) External control + COM control. (5) Operation panel + external + COM control. (6) Operation panel + COM control. (7) COM control. (8) No start or stop operation.
||(1) Current-limiting to start. (2) Voltage ramp to start. (3) Torque control + current-limiting to start. (4) Torque control + voltage ramp to start. (5) Current ramp to start. (6) Voltage current-limiting double closed-loop start.
||(1) Soft stop. (2) Free stop.
||(1) Open loop protection for external instantaneous stop terminals. (2) Over-heat protection for soft starter. (3) Protection for too long starting time. (4) Input open phase protection. (5) Output open phase protection. (6) Unbalanced three-phase protection. (7) Starting over current protection. (8) Running overload protection. (9) Under voltage protection for power voltage. (10) Overvoltage protection for power voltage. (11) Protection for fault parameter setting of the soft starter. (12) Load short circuit protection. (13) Auto restart or incorrect wiring protection. (14) Incorrect wiring protection of external control stop terminals.
||Place to be used
||Indoor location with good ventilation free from corrosive gas and conductive dust.
||Below 1000M. It has to increase the soft starter rate power when the altitude is more than 1000M.
||-30 +55 oC
||90%RH without dew condensation.
||Natural wind cooling.
Tips: Can a soft starter control the induction motor in variable speed?
A soft starter can NOT control induction motor speed, it only restricts motor starting current by applying the voltage in a ramp to avoid inrush current impact on the motor. To vary the speed, you should go for a variable frequency drive which can control the induction motor speed along with starting torque, but cost much more than a soft starter. The selection between VFD and soft starter depends on lots of factors, you can check our blog post regarding VFD vs Soft Starter for details.
Write your own review for 75 hp (55 kW) Soft starter, 240v/440v/480v/660v