The main breaker should be sized ad 150% of the motor Full load current, the overload should be sized at 115% or 125% of the Full load current that depends on the service factor. You conductors can be sized at 125% of the motor full load current, and the contactors can be sized at 58% of the motor full load current for the main and delta contactors and 38% for the star contactor.
Normally I would just use contactors of the same value but some engineers use that calculation. Reason the using a smaller contactor then the motor for delta and main is because when the motor makes the change to delta the current splits in half between both contactors.
Leave your comment (Registered user only)